Our classic stove Grand’Ovale 2dn size can be used as waterstoves, replacing the air exchanger with a properly built water exchanger, and connecting it to the radiators.
The stove will then perform the boiler function in all respects and it can be positioned in a central area of the home, enjoying in addition to its efficiency, even its beauty.
The thermo-sanitary system must be executed and certified in a professional manner by a professional so as to guarantee its safety and functioning.
|Models & Size||Grand’Ovale Size 1°||Vienna Size 2° / Grand’Ovale Size 4° - 5°|
|Output to the water||kW||4||5|
|Output to the room||kW||5||9|
|Carbon monoxide emissions % CO 13% O2||%||0.06||0.17|
RECOMMENDED SCHEME FOR THE INSTALLATION OF THE WATERSTOVES
1. Waterstove La Castellamonte on models: Vienna 2nd size, Grand’Ovale 1st, 4th and 5th size
2. Open expansion vessel with float
3. Overflow drain
4. Network water
5. Insulated hose min. 1 inch
6. 1-inch charging hose
7. 1-inch flow tube
8. 1 inch return tube
9. Circulating pump
10. Thermal probe for circulation pump start
11. Waterstove electronic control
12. Waterstove drain
15. Storage tank